Engine/Pump room bilge high level alarm system
IMO MSC. 67 and the OCIMF International Petroleum Forum stipulates that all pumping chambers on tankers for new and existing tankers should be equipped with high-level alarms for guards with hearing and visible alarms.
Structure and principle of operation of the system
The BOA-2000 includes a level sensor and control cabinet. It monitors the level of the watchdog well and triggers sound and image alarms by sending a signal to the control cabinet when the la canh level reaches the set value.
|Sensor type||Buoy sensor||Electrolynthynity Sensor|
|Source||Max 250 VAC, 0.5 A||Max 250 VAC, 0.5 A|
|Connect||Connection||JIS 5K 50 A|
|Installation point||120 – 5000mm||120 – 550mm|
|IP protection level||IP56||IP 56|
|Explosion room certification||Ex Protection||Ex ia IIC T6|